Add new FAQ
Add Search Word
Which Energy Meters can be connected to ZS/S1.1?
ZS/S 1.1: The red error indicator (LED) is blinking or permanently ON. What can I do?
Which parameters must be set in ETS application of ZS/S1.1 according to connected meters?
What is the maximum communication speed (baud rate) if data from meter are read/sent via IR-Interface to ZS/S1.1?
Is it possible to set the primary address of a meter within the webUi of QA/S3.x.1?